FACTORIES AND MACHINERY (STEAM BOILER AND
UNFIRED PRESSURE VESSEL)
PART III - UNFIRED PRESSURE VESSELS
Regulation 60. Installation.
(1) Every stationary unfired pressure vessel shall be installed so as to give sufficient space
between it and any other machinery, wall, ceiling or column, for inspection and repairs. No part
thereof shall be encased in concrete or earth.
(2) Every stationary vertically mounted unfired pressure vessel shall be clear of the floor or
ground by a distance not less than six inches.
(3) An air receiver shall only be mounted vertically where the lower end is dished concave to
pressure so as to allow proper drainage.
Copyright © 2004 PNMB-LawNet. All rights reserved.