FACTORIES AND MACHINERY (STEAM BOILER AND
UNFIRED PRESSURE VESSEL)
Regulation 20. Low-water alarm.
Every low-water alarm fitted to a steam boiler shall-
(i) be so constructed that it may be adjusted after fitting; and
(ii) be adjusted so that the alarm is sounded when the water level is visible in the gauge
Copyright © 2004 PNMB-LawNet. All rights reserved.