FACTORIES AND MACHINERY (STEAM BOILER AND
UNFIRED PRESSURE VESSEL)
Regulation 19. Low-water fuel cut-out.
(1) Every steam boiler low-water fuel cut-out shall be connected to the burner control system so
that when the water falls below its safe working level such burner shall be shut down pending
(2) Every low-water cut-out shall be so constructed as to be readily blown down, cleaned,
inspected and tested.
(3) The internal parts of every low-water cut-out shall be made of material resistant to corrosion.
Copyright © 2004 PNMB-LawNet. All rights reserved.